Page:Incandescent electric lighting- A practical description of the Edison system.djvu/118

 have also the advantage of quick steaming under heavy changes in load.

We have to-day brought before us in the underground systems the consideration of what is to most of the companies their most serious problem, in the proper solution of which the best talent is being devoted. In the Edison underground system we have what is generally recognized as the most practical solution for circuits of less than 400 to 500 volts. We here obtain at a premium of cost the most flexible system and local distribution from house to house, which has no equal It enables you to take off services for local distribution from every twenty feet without in any way affecting the insulation on the main line, and being able at any time to disconnect these services and restore the main to its original condition. In any other system we have the problem of splicing and cutting of cables, which, at its best, is bad work. What we desire is not such a high insulation as good mechanical protection. As long as we can hold a moderate